Brass Push-to-Connect Fittings FAQs
What are SharkBite push-to-connect fittings?
SharkBite push-to-connect fittings are the core products within the SharkBite System, and provide the easiest and most dependable way to join PEX, copper, CPVC, HDPE or PE-RT pipe in any combination without solder, clamps, unions or glue. When you insert the pipe, the stainless steel teeth in our push-to-connect fittings bite down and grip tight, while the specially formulated o-ring compresses to create a perfect, secure seal. Browse our brass push products.
What is the pipe insertion depth for the SharkBite fittings?
Are SharkBite fittings approved for use behind-the-wall?
SharkBite push-to-connect fittings are certified for use within a concealed wall, but consulting with local plumbing codes is recommended for specific applications. It is also recommended to pressure test the system prior to sealing up the wall. Read more about behind-the-wall applications.
Are SharkBite fittings approved for underground use?
Do I need tools to connect SharkBite fittings?
No. You don't need any specialized tools to connect SharkBite fittings. Although, the SharkBite Deburr & Gauge Tool is recommended for deburring and measuring the depth of the pipe. The pipe must be cut square, deburred and free of debris before installing.
Do I need the Disconnect Clip to remove a SharkBite fitting?
Are SharkBite fittings reusable?
Yes. SharkBite fittings can be reused for testing purposes but any fitting used repeatedly for testing should not be used in a permanent installation.
Can a SharkBite fitting be rotated on the pipe?
Yes. SharkBite fittings can be rotated after installation. Rotating the fitting will not affect the integrity of the joint.
Can I use SharkBite fittings for anything other than potable water and radiant heating (e.g, air, gas, oil, etc.) applications?
No. SharkBite fittings are only certified for potable water & radiant heating installations.
What is the maximum temperature and pressure rating for SharkBite fittings?
SharkBite fittings are certified to 200 PSI and 200°F (93°C).
What types of pipe can SharkBite fittings be used with?
SharkBite fittings are certified for use with:
- Copper pipe hard drawn Type K, L and M and annealed Type M not to exceed 3/8 nominal, complying with ASTM B88
- PEX pipe complying with ASTM F876 or CSA B137.5
- CPVC pipe complying with ASTM D2846 or CSA B137.6
- PE-RT pipe complying with ASTM F2769
- HDPE pipe complying with ASTM D2737 (SDR-9)
Can SharkBite fittings be used with soft copper or rolled copper?
No. SharkBite fittings can only be used with hard drawn copper types K, L, and M.
Can the tube liner be removed?
Yes. The tube liner can easily be removed by pulling it past the o-ring, with the aid of the SharkBite Disconnect Clip or Disconnect Tongs (both sold separately). The tube support liner can drop out of the fittings as it can move freely past the grab ring. Needle nose pliers may be used to pull the tube support liner out.
NOTE: The tube liner is necessary for use with PEX, HDPE or PE-RT Pipe. It is not required for copper or CPVC, however, it is not necessary to remove the tube liner from the fitting.
What should I do if a SharkBite system is leaking upon installation?
SharkBite fittings can leak due to one of these reasons:
- The pipe was not properly deburred prior to installation.
- The pipe was not properly inserted.
- The pipe was not squarely cut.
- The pipe has scratches or debris on the outside that is preventing the O-ring from getting a watertight seal.
How well do SharkBite joints hold up in freezing temperatures?
Water systems should not be allowed to freeze. When water freezes, it expands and creates pressure that exceeds plumbing system pressure capabilities, i.e. pipes and fittings burst.
How far away from a SharkBite joint do I need to be in order to solder?
It is recommended to solder any joints prior to installing a SharkBite fitting. The heat from the torch can be transferred through the pipe and potentially damage the O-ring.
Are SharkBite fittings certified for hydronic heating applications?
Yes. SharkBite fittings can be used for hydronic heating applications if the temperature does not exceed 200°F.
NOTE: Glycol mixture for hydronic is acceptable up to and including 100%.
Do you need a tube liner with SharkBite large diameter fittings?
Yes. A tube liner is required when using the SharkBite large diameter fittings in conjunction with PEX, PE-RT or HDPE pipe. Tube liners are not required when using SharkBite large diameter fittings with copper or CPVC. The large diameter tube liners are sold separately.
Can I use SharkBite fittings as a dielectric union?
Depends on the item. The standard SharkBite fittings (i.e. Coupling, Elbow, Tee) cannot be used as a dielectric union. However, SharkBite Stainless Steel Braided Flexible Coupling Hoses can be used as a dielectric union.
What standards & codes do SharkBite fittings comply?
To view the full list of SharkBite brass push approvals, visit a product page for one of our Brass Push products. SharkBite fittings are compliant with the Uniform Plumbing Code (UPC), National Plumbing Code of Canada and the International Plumbing Code (IPC). Since local code varies by area, please consult with local plumbing codes for specific applications.
How long can a SharkBite fitting last?
SharkBite fittings and PEX pipe carry a 25-year warranty against any manufacturer’s defect as long as the item has been installed in accordance with the installation instructions and complies with local code. For more information, read our full SharkBite Warranty.
Have comments or questions?